The Hidden Kitchen
Understanding the Structure of a Modern Kitchen
Putting together a kitchen is not a trivial process. Besides the obvious considerations: new cabinets, appliances, a new floor, and paint or wallpaper, there are many structural considerations.
The kitchen structure is hidden — behind cabinets, under floors, above ceilings — and not very pretty, but extremely important. Without adequate electricity, lighting, plumbing, heating, and venting — all the new cabinets and appliances won't result in a workable or safe kitchen.
So, let's take a look at kitchen structure.
Almost all kitchens more than 10 years old are under-powered. Electricians and builders of old simply could not predict the number of large and small appliances found in most kitchens today. Depending on the age of your house, you can expect only one or two receptacle circuits, with illumination pulled from a general lighting circuit powering all ceiling lights. Safety is another important issue, as most older kitchens do not have ground-fault-protected circuits that are absolutely required by safety codes today.
Ground-fault circuit interrupters (GFCI) outlets help to avoid accidental electrocution by shutting off the electrical current in you Accidentally touch a live wire. According to the National Electrical Code, all outlets within 6 feet of a water source and all receptacles serving kitchen countertops and islands must have GFCI protection. Best practice, however, is to GFCI-protect all kitchen outlets.
Electrical Requirements for a Modern Home Kitchen
|Lighting, Ambient||110v, 15 amp||1||General room lighting, usually with ceiling lamps.|
|Lighting, Task||110v, 15 amp||1||Work area lighting, generally undercabinet fluorescent or LED lighting.|
|Over Counter Outlets||110v, 20 amp||2||Even in small kitchens, two separate circuits to counter outlets is a good idea. In large kitchens, it may be required by your local electrical code.|
|Electric Range or Cooktop||220v||2||Gas range: 110v, 15 amp.|
|Wall Oven||220v||2||Gas wall oven: 110v, 15 amp.|
|Microwave Oven||110v, 20 amp||1||If combined with the range vent, both can use the same circuit.|
|Refrigerator||110v, 20 amp||1|
|Freezer||110v, 20 amp||1||Stand-alone freezer separate from the refrigerator|
|Trash Compacter||110v, 20 amp||1||Some localities allow the compactor to share a circuit with the disposer.|
|Dishwasher & Disposer||110v, 20 amp||1||Some localities require a separate circuit for each appliance.|
|Instant Hot Water Dispenser||220v||2||Some instant hot water dispensers use 110v, 20 amp power.|
1. Slots required in your service panel. A 220-230v circuit requires two service panel breaker slots. A 110-120v circuit requires one.
2. The total number of circuits required for the typical modern kitchen nearly equals the number needed for the whole house just 50 years ago.
In a complete kitchen overhaul, upgrading the wiring is fairly easy, if there is enough room for new breakers in the service panel. Often the panel is too small. Lacking enough room for expansion, a panel and service upgrade is a must. The job will run $600 to $1,200 in most markets and is always money well spent.
As for powering a new kitchen, large appliances that produce either heat or cold need their own dedicated circuits. This includes the refrigerator, microwave, and dishwasher, although in most areas it is permissible to combine a dishwasher and food disposer on one circuit..
Avoid plugging a computer into a circuit that is serving a spike producing microwave oven — unless you just like the interesting on-screen effects. Electric ranges, cook-tops, and ovens each require their own 220-volt circuit.
If your kitchen is large enough, try to power the above-counter receptacles with two 20-amp circuits. These usually serve small appliances like blenders, coffee makers, and microwaves that will appreciate the extra power — and show their appreciation by not overloading and tripping the circuit breaker..
The best practice, not always followed, is to power every other outlet above a countertop from a different circuit. This ensures that at least some outlets have power if one circuit fails, something that only seems to happen when you are in the middle of fixing Thanksgiving dinner.
Most electrical codes require an above-counter duplex outlet a minimum of every four feet — closer is better, of course — and it usually costs very little more to install four-plex rather than duplex outlets, doubling your plug-in capacity..
As a general rule, when in doubt, and when possible, provide more, not less electricity. If the last 50 years are any guide, the kitchen of the future will require even more power than today's kitchens.
If you have an appliance garage, include an outlet or two inside the garage. The allows you to leave the appliances plugged in so you need only pull them out to use them.
Outlets inside cabinets can power a television and stereo equipment. Consider your lighting needs too. That dark cavern under the sink can be well lit by a 40-watt bulb in a simple pull-chain fixture under the sink.
Most kitchens are poorly lighted. The light from a single fixture centered overhead is usually blocked by your own body as you work at the counter. Wall cabinets also block overhead light, leaving the primary food-prep spaces darker than the rest of the room.
It's not just the age of the kitchen that matters — it's also the age of the cook. Experts say that people over the age of 50 require at least twice as much light to read than they did when they were 20. The solution? More versatile, task-oriented light in more places.
Fluorescent under cabinet lights can make a big difference and cost very little to install and operate. Expect a typical fixture to cost less than $25. Not every cabinet will need a fluorescent light, but those nearest your primary workspaces should have them. For even more lifetime cost savings, use LED undercabinet lights. The initial cost may be a little higher, but the life-cycle cost much lower. LEDs use much less electricity for the same amount of illumination, and, as a bonus, last several times longer than fluorescent lamsp.
Recessed CFL or LED fixtures can also brighten a workspace inexpensively and do double duty when controlled by a dimmer switch. At full power, they're task lights, at one-third power they're accent lights.
Recessed ceiling fixtures are also popular for general room lighting. They can be spread out to direct light to every corner of the room. If you live in a single story house, opt for the slightly more expensive zero-clearance models. These can stand direct contact with attic insulation. Fixtures that are not zero-clearance need ventilation to keep the lamps and wiring cool, and if surrounded by insulation may bet hot enough short the fixture or, worse, start a fire.
Cove lighting is another popular option for general illumination. Inexpensive fluorescent fixtures are installed on top of cabinets airmed at the ceiling. The light reflected off of the ceiling illuminates the room with an even, soft glow. To aid the process, we usually install a reflective foil surface on the top of the cabinets.
Line voltage (110v) fixtures are declining in popularity. The small but mighty low-voltage LED alternatives are gaining ground pretty quickly. Their advantages are compact design, energy efficiency, and a certain minimalist understatement.
Some fixtures are so compact that they fit invisibly beneath wall cabinets and even inside dinnerware and curio cabinets. Some fixtures have their own voltage reducing transformers, while in other cases, several fixtures are ganged together. A 100-watt transformer, for example, could serve five 20-watt lamps. Some of the small fixtures come in strip light form, with lamps in fixed positions, while miniature tracks allow a variety of twist-in lamp holders.
The disadvantages? These small lights are expensive, often costing four to five times that of standard incandescent fixtures.
When planning your lighting, keep in mind that the old standard Type-A incandescent light bulb is now banned. The alternatives are compact fluorescent and LED bulbs designed to fit in a Type A (or Edison) socket.
Read more about efficient kitchen lighting design in Designing Efficient and Effective Kitchen Lighting.
The piping in your kitchen may also in bad shape. If your kitchen is over 50 years old, it's a good bet that the original piping was made of galvanized steel, an excellent product with a long lifespan. But it is now nearing the end of its useful life, and time to replace it with plastic, which, as far as we know, lasts forever.
There is also close to a 100% chance that the original plumbing does not meet current plumbing code requirements. Any time you touch kitchen plumbing, you are going to have to bring it up to current code. In most localities, this is true even if you otherwise would not need to disturb a pipe. But, irrespective of code requirements, its always better to update plumbing while the room is empty and the walls open rather than waiting for the very expensive repair that is sure to come a few years down the road if deteriorating plumbing is left in place.
One of the common plumbing problems we find is a badly sloped drain line. The ideal slope for any horizontal drain line is 1/4" per linear foot. This much drop allows the waste-bearing water to move slowly enough to carry solids along with the flow but swiftly enough to scour the side walls of the drain pipes. We find slopes as little as 1/16" per foot, which almost guarantees clogging and periodic emergency calls to the plumber.
Oversloping is also a problem and a common mistake made by DIY plumbers (is some slope is good, more slope is better, right?). Slopes much greater than the ideal 1/4" are as likely to clog as undersloped pipes because the liquids move too fast and leave the solids behind. Proper sloping is critical with disposer dumping solid waste into the drain system.
Inadequate drain venting is another frequent problem. Drain pipes must be vented to the atmosphere outside of the house to work properly (not to be confused with room venting, discussed below).
It's easy to illustrate the problem caused by inadequate venting using the "Pepsi Challenge".
Pop the top on a can of Pepsi and turn it upside down to drain. It will drain with a glug-glug-glug sound. As the liquid drains a vacuum is formed at the top of the can (or bottom of the can since it is now upside-down). Nature abhors a vacuum and tries to fill it with something. The only thing available is air, so air is sucked up into the can through the only opening available — the same hole through which the soda is draining. The brief pause between one glug and the next is the air entering the can. Now take your handy awl from your toolbox and punch a small hole in the top (actually the bottom) of the can. The soda immediately pours out in a rush. Air now has an easier way of getting into the can through the small hole you just made, so it no longer has to fight with the liquid to use the drain hole.
Venting in your plumbing system works exactly the same way. It allows air to enter the system to fill any vacuums created by draining liquids. And, perhaps most importantly, it allows any methane that builds up in your drains to escape safely to the outside. Methane is just natural gas without the bad smell. In fact, it is odorless, and since it is very flammable and can easily explode, it is also very dangerous.
This is why modern plumbing codes no longer permit venting directly through a wall (the gas may be sucked into an upstairs window) or into the attic. If enough accumulates in the attic, it may explode. Vents must terminate outside and above the roof line.
Many older kitchens sinks were vented through a drain from an upstairs bathroom. This is not a good method since, as in our Pepsi example, if water is draining from upstairs, the air and water are fighting for space in the drain pipe, so venting is inadequate. Most plumbing codes no longer allow these "wet vents" except in exceptional circumstances, so we have to add a vent for the kitchen sink that does not share a pipe with water.
If you install an island cabinet with a sink, the drain line serving that sink often cannot be vented conventionally. In this case, an automatic-vent device or a barometric (loop) vent is required. A licensed plumber will know which is best for your situation. In Nebraska, and many other localities, automatic vent devices are not allowed because they tend to fail after a few years.
Changes in the house heating and air conditioning systems are usually not required to remodel a kitchen in an existing space. But if a bumpout or addition is built, then additional heating and cooling may be required.
Sometimes, the only solution is to upgrade the whole house system, which can get a little pricey. But this is rare. What we usually do is add a supplemental system on its own thermostat to heat and cool the additional space. The new kitchen "zone" can be controlled separately from the rest of the house, which is nice when the oven is pouring out heat on a summer day.
What will almost always be required, however, is a new exhaust vent over the cooking surfaces. Few older exhaust systems meet current building code requirements, and building code requirements are themselves probably inadequate to ensure that modern kitchens are well vented.
Install a range hood that vents to the outside. Cooking on a range or cooktop releases ultra-fine particles of grease, water, smoke and food into the air that land everywhere, which explains the grime that accumulates on cabinets, fllors and fabrics. The notion that a ventless (recirculating) range hood can actually trap the estimated 200 lbs. per year of particulates produced by cooking in the average kitchen is just plain nonsense. Nor do they exhaust the humidity produced by cooking or the chemicals that may result from the incomplete combustion of natural gas including nitrogen dioxide which has been shown to cause respiratory problems, including elevated asthma, especially in children. Most building codes now require venting to the outside, either through a wall or the roof. Through the wall venting has a number of restrictions, so check your local building code.
A kitchen vent hood should be able to completely exchange the air in your kitchen at least 15 times each hour or once every 4 minutes. The capacity of the kitchen vent fan required is based on the size of the kitchen, the maximum amount of heat produced by the range or cooktop and the length and configuration of the ductwork. Its a fairly complicated calculation that a HVAC contractor will complete before recommending a minimum capacity.
The length and configuration of the ducting used to exhaust the contaminated air to the outside requires more venting capacity for a longer pipe and that capacity be added for each bend in the pipe. For example, hen using smooth, round 8” diameter metal pipe, one cubic foot per minute of capacity is added for each foot of pipe, plus 25 CFM for each elbow, and 40 CFM for a roof cap.
Research by the University of Minnesota's Sustainable Houseing Initiative has shown that most existing range hoods to be too small, too high, or not oriented properly to do their job. The most effective hoods are at least as wide as the cooktop, preferably wider, extend at least 20" beyond the front edge of the range, and are rectangular rather than angled or curved in front. Most wall-mounted hoods extend no further than the to the center of the front burners, considerably less than the projection recommended by the stury.
Consumer Reeports recommends that an island microwave be at least 6" larger in each direction than the cooktop or range it vents. Few hoods designed for residential kitchens meet these minimums.
Downdraft vents are even more problematic. They work by pulling the air sideways across the cooking surface and drawing smoke, steam and grease down through a filter and into a duct that carries it beneath the floor to an exterior vent. To be effective they must struggle against the the natural tendency of warm cooking gases and particles to rise. Most project about 10" above the cooking surface and without a hood to capture steam and gases and direct them to the fant, they rely on a large fan capacity to work well.
Hoods that are integrated with microwaves mounted over the range are a particular problem. These typically extend over Just the back half of the range and miss most of the contaminants generated by front burners. Consumer Reports found that none of the microwave-vents tested for its most recent report were top-rated for effective ventilation. One solution is to enlarge the capture zone by installing an extension that attaches to the front of the microwave.
The Home Ventilating Institute (HVI) recommends a ventilation rate of 100 CFM per linear foot of range placed against a wall and 150 CFM when placed above an island.2 These levels will ensure that enough air is being pulled from the system to help maintain healthy indoor air quality. A typical 30" range (2.5 feet) should vent at a rate of 250 CFM.
Generally, local building codes require a capacity of at least 150 CFM, and most areas require makeup air if the capacity exceeds 350 CFM. This may require a servo-operated intake vent located (usually) in the basement that automatically opens when the fan is turned on.
Consider two useful ventilation features: a heat recovery system and automatic vent operation:
- Heat Recovery Ventilator: When your vent fan removes all the air from your kitchen and replaces it with outside air - it is also removing all the heat in the air, which typically just gets blown outside. In the summer, this is a godsend, but in winter you don't want to waste the heat. You can recover most of this heat with a heat recovery ventilation (HRV) system that acts as a heat exchanger, extracting any heat leaving the house and using it to heat make-up air coming into the house.
These systems require a heat exchanger, usually mounted in an attic, and two ducting systems, one to exhaust contaminated air and and another to being in fresh air. Both are run through the heat exchanger where the heat from the outgoing aire is conveyed to the incoming air.
For more information on range vent heat recovery, see Heat Recovery Ventilation by the Cold Climate Housing Research Center.
- Automatic Ventilation: You might also give a thought to the various automatic switches to control the ventilator fan. The one we like best activates the vent the fan when any burner on the range is turned on. Another senses the heat above the range and turns on the vent fan when it determines that a burner has been lit — excellent for gas ranges.
Kitchen Design Guidelines
Structural considerations are a major part of any designer's kitchen planning. Many are contained in the Kitchen Design Guidelines published by the National Kitchen & Bath Association. Starting in 1944 the University of Illinois conducted a number of studies of kitchen design and developed fundamental design principles that are still very much in use today. A kitchen that follows all of these rules is almost guaranteed to be both functional and safe. See how many rules your existing kitchen violates for a better understanding of why it may seem awkward and dysfunctional… (Continues)10/20/18[08/27/18]